All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
This advisory is a follow-up to ICS-ALERT-10-362-01—Ecava IntegraXor DLL Hijacking.
ICS-CERT has become aware of a Uncontrolled Search Path Element vulnerability, commonly referred to as DLL Hijacking, in the Ecava IntegraXor supervisory control and data acquisition (SCADA) product. ICS-CERT has worked with Ecava to validate the vulnerability.
Ecava has developed a patch release for IntegraXor to address this vulnerability. ICS-CERT has validated the patch.
This vulnerability affects all IntegraXor versions prior to Version 3.60 (Build 4090).
A successful exploit of this vulnerability leads to arbitrary code execution. The impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Ecava Sdn Bhd is a Malaysia-based software development company that provides the IntegraXor SCADA product. Ecava specializes in factory and process automation solutions.
IntegraXor is a suite of tools used to create and run a web-based human-machine interface for a SCADA system.
IntegraXor is currently used in several areas of process control in 38 countries with the largest installation based in the United Kingdom, United States, Australia, Poland, Canada, and Estonia.
IntegraXor is vulnerable to DLL Hijacking. An attacker may place a malicious DLL in a directory that is loaded before the valid DLL. An attacker must have access to the computer’s file system to exploit this vulnerability.
--------- Begin Update B Part 1 of 2 ----------
This vulnerability may be exploitable from a remote machine. If exploited, this vulnerability may allow execution of arbitrary code.
--------- End Update B Part 1 of 2 ----------
Existence of Exploit
No known exploits specifically target this vulnerability.
An attacker requires a moderate skill level to exploit this vulnerability.
ICS-CERT recommends that users of Ecava IntegraXor take the following mitigation steps:
- Update IntegraXor to the latest version and install the latest patch 3.60 (Build 4090).
Ecava has developed and released a patch to mitigate the vulnerability. The patch can be downloaded from:
--------- Begin Update B Part 2 of 2 ----------
--------- End Update B Part 2 of 2 ----------
ICS-CERT encourages asset owners to minimize network exposure for all control system devices. Critical devices should not directly face the Internet. Locate control system networks and remote devices behind firewalls and isolate them from the business network. When remote access is required, use secure methods, such as VPN, recognizing that VPN is only as secure as the connected devices.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
The Control Systems Security Program (CSSP) also provides a section for control system security recommended practices on the CSSP web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.