All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
Siemens has reported to ICS-CERT that denial-of-service (DoS) vulnerabilities exist in the SIMATIC S7-400 V6 and SIMATIC S7-400 V5 PN CPU products. Siemens has produced a firmware update that mitigates the vulnerability affecting the S7-400 V6.
Siemens will not fix the vulnerability that affects the S7-400 V5 because that product version has reached end-of-life and has been discontinued.
Both vulnerabilities could be exploited remotely.
Siemens reports that one of the vulnerabilities affects the following products within the S7-400 CPU family with firmware Versions 6.0.1 and 6.0.2
- CPU 412-2 PN (6ES7412-2EK06-0AB0)
- CPU 414-3 PN/DP (6ES7414-3EM06-0AB0)
- CPU 414F-3 PN/DP (6ES7414-3FM06-0AB0)
- CPU 416-3 PN/DP (6ES7416-3ES06-0AB0)
- CPU 416F-3 PN (6ES7416-3FS06-0AB0)
Another vulnerability affects the following products within the S7-400 CPU family with firmware Version 5:
- CPU 414-3 PN/DP (6ES7414-3EM05-0AB0)
- CPU 416-3 PN/DP (6ES7416-3ER05-0AB0)
- CPU 416F-3 PN/DP (6ES7416-3FR05-0AB0)
When specially crafted packets are received on Ethernet interfaces by the SIMATIC S7-400, the device can default into defect mode. A PLC in defect mode needs to be manually reset to return to normal operation.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Products in the Siemens SIMATIC S7-400 CPU family have been designed for process control in industrial environments such as manufacturing, power generation and distribution, food and beverages, and chemical industries worldwide.
Denial of Service1
When the Ethernet port on a SIMATIC S7-400 V6 receives a malformed IP packet, the device could go into the defect mode. The SIMATIC S7-400 V6 CPU defect mode locks out the unit so that it is not available for process control. An attacker could use this vulnerability to perform a DoS attack.
These vulnerabilities could be exploited remotely.
Existence of Exploit
No known public exploits specifically target these vulnerabilities.
An attacker with a low skill could exploit these vulnerabilities.
Siemens has released security advisories (SSA-589272 and SSA-617264) that detail the vulnerabilities in the two SIMATIC S7-400 CPU and the recommended security practices to secure the systems.
Siemens is not providing a firmware update for SIMATIC S7-400 V5 PN CPUs because this version has reached end-of-life and has been discontinued.
ICS-CERT encourages asset owners to take the following additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
The Control Systems Security Program (CSSP) also provides a section for control systems security recommended practices on the CSSP Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS-CERT Technical Information Paper, ICS-TIP-12-146-01A—Cyber Intrusion Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- 1. CWE-404: Improper Resource Shutdown or Release, http://cwe.mitre.org/data/definitions/404.html, Web site last accessed July 30, 2012.
- 2. CPU 412-2 PN, http://support.automation.siemens.com/WW/view/en/45645157, Website last visited July 26, 2012.
- 3. CPU 414-3 PN/DP, CPU 414F-3 PN/DP, http://support.automation.siemens.com/WW/view/en/45645228, Website last visited July 30, 2012.
- 4. CPU 416-3 PN/DP, CPU 416F-3 PN, http://support.automation.siemens.com/WW/view/en/45645229, Website last visited July 30, 2012.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.