All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
This advisory provides mitigation details for a vulnerability that impacts the Siemens Automation License Manager (ALM).
Siemens ProductCERT has identified an uncontrolled resource consumption vulnerability1 in the Siemens ALM, which is used for license management by various Siemens software products. Siemens has produced a software update that fully resolves this vulnerability. Exploitation of this vulnerability would allow loss of availability of the system.
All Siemens software products that include ALM version between 4.0 and 5.2 are affected. The following Siemens product families are affected:
- SIMATIC (e.g., STEP 7)
- SIMATIC HMI (e.g., WinCC, WinCC flexible)
- SIMATIC PCS 7
- SIMOTION (e.g., Scout)
- SIMATIC NET
- SINAMICS (e.g., Starter)
Attackers could exploit the vulnerability to cause memory leakage within the software. This exploit could eventually lead to a crash of the application. The DoS of the ALM could lead to a DoS of associated devices that use the ALM to verify active licenses.
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of these vulnerabilities based on their operational environment, architecture, and product implementation.
Siemens is a multinational company headquartered in Munich, Germany. Siemens develops products mainly in the energy, transportation, and healthcare sectors.
ALM centrally manages licenses for various Siemens software products. The products contact ALM either locally or remotely to verify their license using a proprietary protocol. To enable this license verification, ALM listens on Port 4410/TCP by default. These products are deployed across several sectors including energy, healthcare, and others worldwide.
Uncontrolled Resource Consumption2
An attacker can send maliciously crafted packets to Port 4410/TCP, which will cause a memory leakage and uncontrolled resource consumption, leading to a DoS.
This vulnerability could be exploited remotely.
Existence of Exploit
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
Siemens has provided an update that resolves this vulnerability. The update can be applied to all versions of ALM starting with version 4.0. Siemens recommends that asset owners and operators can contact Siemens customer support to acquire the update.
Siemens recommends blocking traffic to Port 4410/TCP from external and remote connections.
ICS-CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the US-CERT Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies. ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS-CERT Technical Information Paper, ICS-TIP-12-146-01A—Cyber Intrusion Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- 1. SSA-783261, http://www.siemens.com/corporate-technology/pool/de/forschungsfelder/siemenssecurityadvisoryssa-783261.pdf, Web site last accessed December 14, 2012.
- 2. CWE, http://cwemitre.org/data/definitions/400.html, CWE-400: Uncontrolled Resource Consumption (“Resource Exhaustion”), Web site last accessed December 14, 2012.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.