All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
Adam Crain of Automatak and independent researcher Chris Sistrunk have identified an improper input validation vulnerability in the Software Toolbox TOP Server DNP Master OPC product. Software Toolbox has produced a new version that mitigates this vulnerability. The researchers have tested the new version to validate that it resolves the vulnerability. This vulnerability could be exploited remotely.
The following Software Toolbox products are affected:
- DNP Master Driver for the TOP Server OPC Server (Version 184.108.40.206) and earlier.
The master station can be sent into an infinite loop by sending a specially crafted Transmission Control Protocol (TCP) packet or through serial communications. A successful attack exploiting this vulnerability could allow an attacker to put the master station into an infinite loop, causing a denial-of-service condition. The master station must be manually restarted to recover from the loop condition.
Impact to individual organizations depends on many factors that are unique to each organization. ICS‑CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation.
Software Toolbox is a US-based company that maintains offices primarily in North Carolina. The Software Toolbox TOP Server is used for industry and third-party connectivity communication software for automation, both OPC and embedded device communications.
The affected product is a Microsoft Windows-based software that facilitates connectivity to multiple DNP3 compliant devices such as human-machine interfaces, remote terminal units, programmable logic controllers, and meters. According to Software Toolbox, the TOP Server OPC I&C is deployed across several sectors including building automation, power distribution, oil and gas, and water and waste water.
IMPROPER INPUT VALIDATIONa
The Software Toolbox TOP Server DNP Master Driver does not validate input on Port 20000/TCP. This can allow an infinite loop to occur outside the protocol stack, requiring a manual restart to restore communication and control.
This vulnerability could be exploited remotely.
EXISTANCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a moderate skill would be able to exploit this vulnerability.
Software Toolbox has produced a new version of the software, Version 220.127.116.11, which resolves the vulnerability. This version was released June 18, 2013. Information and support about various versions are available at the Software Toolbox Top Server OPC I/O Server support site (registration required):
The most current version of TOP Server available is Version 18.104.22.168 R2 (issued August 5, 2013): http://www.toolboxopc.com/html/support.asp).
The researchers suggest the following mitigations:
- Block DNP3 traffic from traversing onto business or corporate networks through the use of an IPS or firewall with DPN3-specific rule sets.
ICS‑CERT encourages asset owners to take additional defensive measures to protect against this and other cybersecurity risks.
- Minimize network exposure for all control system devices. Critical devices should not directly face the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPN is only as secure as the connected devices.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT Web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.d ICS‑CERT reminds organizations to perform proper impact analysis and risk assessment prior to taking defensive measures.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B—Targeted Cyber Intrusion Detection and Mitigation Strategies,e that is available for download from the ICS-CERT Web page (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS‑CERT for tracking and correlation against other incidents.
In addition, ICS‑CERT recommends that users take the following measures to protect themselves from social engineering attacks:
- Do not click Web links or open unsolicited attachments in email messages.
- Refer to Recognizing and Avoiding Email Scamsf for more information on avoiding email scams.
Refer to Avoiding Social Engineering and Phishing Attacksg for more information on social engineering attacks.
- a. CWE-20: Improper Input Validation, http://cwe.mitre.org/data/definitions/20.html, Web site last accessed August 22, 2013.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2013-2804 , NIST uses this advisory to create the CVE Web site report. This Web site will be active sometime after publication of this advisory.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:M/Au:N/C:N/I:N/A:C, Web site last visited August 22, 2013.
- d. CSSP Recommended Practices, http://ics-cert.us-cert.gov/content/recommended-practices, Web site last accessed August 22, 2013.
- e. Targeted Cyber Intrusion Detection and Mitigation Strategies, http://ics-cert.us-cert.gov/tips/ICS-TIP-12-146-01B, Web site last accessed August 22, 2013.
- f. Recognizing and Avoiding Email Scams, http://www.us-cert.gov/reading_room/emailscams_0905.pdf, Web site last accessed August 22, 2013.
- g. National Cyber Alert System Cyber Security Tip ST04-014, http://www.us-cert.gov/cas/tips/ST04-014.html, Web site last accessed August 22, 2013.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.