All information products included in https://us-cert.gov/ics are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see https://www.us-cert.gov/tlp/.
This updated advisory is a follow-up to the original advisory titled ICSA-15-162-01 RLE Nova‑Wind Turbine HMI Unsecure Credentials Vulnerability that was published June 11, 2015, on the NCCIC/ICS-CERT web site.
Independent researcher Maxim Rupp has identified an unsecure credential vulnerability in the RLE International GmbH Nova-Wind Turbine HMI. RLE has been unresponsive in validating or addressing the alleged vulnerability. ICS-CERT is releasing this advisory to warn and protect critical asset owners of this serious issue.
This vulnerability could be exploited remotely.
The following RLE International GmbH product is affected:
- Nova-Wind Turbine HMI
--------- Begin Update A Part 1 of 2 --------
Plain text credentials can be used to gain unauthorized access to the device. This means that a malicious party could perform any action on the device including change or modify configurations and settings.
--------- End Update A Part 1 of 2 ----------
Impact to individual organizations depends on many factors that are unique to each organization. ICS-CERT recommends that organizations evaluate the impact of this vulnerability based on their operational environment, architecture, and product implementation
RLE International GmbH is a Germany-based company that maintains offices in several countries around the world, including the US, UK, Sweden, and India.
The affected product, Nova-Wind Turbine HMI, is a human-machine interface (HMI) for a wind turbine. This product is used in the Energy Sector.
--------- Begin Update A Part 2 of 2 --------
PLAINTEXT STORAGE OF A PASSWORDa
The Nova-Wind Turbine HMI stores credentials in a plaintext file. If a malicious user recovers this file, then they could use the credentials to authenticate with the HMI and make changes to the configuration.
--------- End Update A Part 2 of 2 ----------
This vulnerability could be exploited remotely.
EXISTENCE OF EXPLOIT
No known public exploits specifically target this vulnerability.
An attacker with a low skill would be able to exploit this vulnerability.
ICS-CERT has attempted on multiple occasions to contact the vendor regarding this serious flaw and have according to our vulnerability disclosure policy now produced this advisory. Insecure credential vulnerabilities create a serious risk to asset owners. ICS-CERT strongly recommends ensuring that the impacted product is not connected to the Internet or any network as this vulnerability is remotely exploitable.
ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page at: http://ics-cert.us-cert.gov/content/recommended-practices. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site (http://ics-cert.us-cert.gov/).
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
- a. CWE-256: Plaintext Storage of a Password, http://cwe.mitre.org/data/definitions/256.html, web site last accessed June 11, 2015.
- b. NVD, http://web.nvd.nist.gov/view/vuln/detail?vulnId=CVE-2015-3951, web site last accessed June 15, 2015.
- c. CVSS Calculator, http://nvd.nist.gov/cvss.cfm?version=2&vector=AV:N/AC:L/Au:N/C:C/I:C/A:C, web site last accessed June 11, 2015.
For any questions related to this report, please contact the CISA at:
Toll Free: 1-888-282-0870
CISA continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.