All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
CVSS v3 9.8
ATTENTION: Remotely exploitable/low skill level to exploit.
Vendor: Schneider Electric
Equipment: InduSoft Web Studio, InTouch Machine Edition
Vulnerability: Missing Authentication for Critical Function
Schneider Electric reports that the vulnerability affects the following InduSoft Web Studio products:
- InduSoft Web Studio v8.0 SP2 or prior, and
- InTouch Machine Edition v8.0 SP2 or prior.
Successful exploitation of this vulnerability could allow an attacker to remotely execute arbitrary commands with high privileges.
Schneider Electric recommends users using InduSoft Web Studio v8.0 SP2 or prior should upgrade and apply InduSoft Web Studio v8.0 SP2 Patch 1 as soon as possible. This patch can be found on the Schneider Electric InduSoft web site at the following location:
Schneider Electric recommends users using InTouch Machine Edition v8.0 SP2 or prior should upgrade and apply InTouch Machine Edition v8.0 SP2 Patch 1 as soon as possible. This patch can be found on Schneider Electric’s Invensys web site at the following location (registration required):
For more information on this vulnerability and associated patch, please see InduSoft Security Bulletin LFSEC00000121 on the Schneider Electric cybersecurity web site:
NCCIC/ICS-CERT recommends that users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
ICS-CERT reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
ICS-CERT also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available in the ICS‑CERT Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies, that is available for download from the ICS-CERT web site.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to ICS-CERT for tracking and correlation against other incidents.
No known public exploits specifically target this vulnerability.
InduSoft Web Studio provides the capability for an HMI client to trigger script execution on the server for the purposes of performing customized calculations or actions. A remote malicious entity could bypass the server authentication and trigger the execution of an arbitrary command. The command is executed under high privileges and could lead to a complete compromise of the server.
Aaron Portnoy, formerly of Exodus Intelligence, discovered and reported this vulnerability to ICS-CERT.
Critical Infrastructure Sectors: Critical Manufacturing, Energy, Healthcare and Public Health, Water and Wastewater Systems
Countries/Areas Deployed: Worldwide
Company Headquarters Location: Paris, France
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.