All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: NetComm Wireless
- Equipment: 4G LTE Light Industrial M2M Router
- Vulnerabilities: Information Exposure, Cross-site Request Forgery, Cross-site Scripting, Information Exposure through Directory Listing
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow for the exposure of sensitive information.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
The following versions of the 4G LTE Light Industrial M2M Router (NWL-25), a cellular router, are affected:
- 4G LTE Light Industrial M2M Router (NWL-25) with firmware 126.96.36.199 and prior.
3.2 VULNERABILITY OVERVIEW
The device allows access to configuration files and profiles without authenticating the user.
A cross-site request forgery condition can occur, allowing an attacker to change passwords of the device remotely.
The device is vulnerable to several cross-site scripting attacks, allowing a remote attacker to run arbitrary code on the device.
The directory of the device is listed openly without authentication.
- CRITICAL INFRASTRUCTURE SECTORS: Communications
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Australia
Aditya K. Sood reported these vulnerabilities to NCCIC.
NetComm Wireless has released a new firmware version to mitigate the vulnerabilities. Affected users may download the firmware from: https://support.netcommwireless.com/product/nwl-25#Firmware
NCCIC recommends users take defensive measures to minimize the risk of exploitation of this vulnerability. Specifically, users should:
- Minimize network exposure for all control system devices and/or systems, and ensure that they are not accessible from the Internet.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.