All information products included in http://ics-cert.us-cert.gov are provided "as is" for informational purposes only. The Department of Homeland Security (DHS) does not provide any warranties of any kind regarding any information contained within. DHS does not endorse any commercial product or service, referenced in this product or otherwise. Further dissemination of this product is governed by the Traffic Light Protocol (TLP) marking in the header. For more information about TLP, see http://www.us-cert.gov/tlp/.
1. EXECUTIVE SUMMARY
- CVSS v3 9.8
- ATTENTION: Exploitable remotely/low skill level to exploit
- Vendor: WAGO
- Equipment: Industrial Managed Switches 852-303, 852-1305, and 852-1505
- Vulnerabilities: Use of Hard-coded Credentials, Use of Hard-coded Cryptographic Key, Using Components with Known Vulnerabilities
2. RISK EVALUATION
Successful exploitation of these vulnerabilities could allow a compromise of the managed switch, resulting in disruption of communication, and root access to the operating system.
3. TECHNICAL DETAILS
3.1 AFFECTED PRODUCTS
WAGO reports these vulnerabilities affect the following industrial managed switches:
- 852-303: All versions prior to v1.2.2.S0
- 852-1305: All versions prior to v1.1.6.S0
- 852-1505: All versions prior to v1.1.5.S0
3.2 VULNERABILITY OVERVIEW
An attacker with access to the hard-coded credentials may gain access to the operating system of the managed switch with root privileges, which may allow manipulation of the operating system of the managed switch.
An attacker with access to the hard-coded SSH key may disrupt communication or compromise the managed switch. The SSH-keys cannot be regenerated by users and all switches use the same key.
3.2.3 USING COMPONENTS WITH KNOWN VULNERABILITIES
The listed managed switches use outdated third-party components with known vulnerabilities. See the full list of CVE identifiers in CERT@VDE advisory number VDE-2019-013.
- CRITICAL INFRASTRUCTURE SECTORS: Commercial Facilities
- COUNTRIES/AREAS DEPLOYED: Worldwide
- COMPANY HEADQUARTERS LOCATION: Germany
T. Weber of SEC Consult Vulnerability Lab reported these vulnerabilities to CERT@VDE.
WAGO recommends users update their managed switch to the latest firmware published June 7, 2019, or later. New firmware can be requested in the Runtime Software dropdown within the Downloads section at the links below:
- 852-303: v1.2.2.S0 or later
- 852-1305: v1.1.6.S0 or later
- 852-1505: v1.1.5.S0 or later
WAGO also recommends users implement the following security measures:
- Restrict network access to the switch
- Restrict network access to the SSH server.
- Do not directly connect the device to the Internet.
For more information CERT@VDE has released a security notification which can be viewed at the following link:
NCCIC recommends users take defensive measures to minimize the risk of exploitation of these vulnerabilities. Specifically, users should:
- Implement access control lists.
- Locate control system networks and remote devices behind firewalls, and isolate them from the business network.
- When remote access is required, use secure methods, such as Virtual Private Networks (VPNs), recognizing that VPNs may have vulnerabilities and should be updated to the most current version available. Also recognize that VPN is only as secure as the connected devices.
NCCIC reminds organizations to perform proper impact analysis and risk assessment prior to deploying defensive measures.
NCCIC also provides a section for control systems security recommended practices on the ICS-CERT web page. Several recommended practices are available for reading and download, including Improving Industrial Control Systems Cybersecurity with Defense-in-Depth Strategies.
Additional mitigation guidance and recommended practices are publicly available on the ICS-CERT website in the Technical Information Paper, ICS-TIP-12-146-01B--Targeted Cyber Intrusion Detection and Mitigation Strategies.
Organizations observing any suspected malicious activity should follow their established internal procedures and report their findings to NCCIC for tracking and correlation against other incidents.
No known public exploits specifically target these vulnerabilities.
For any questions related to this report, please contact the NCCIC at:
Toll Free: 1-888-282-0870
The NCCIC continuously strives to improve its products and services. You can help by choosing one of the links below to provide feedback about this product.